mvi56e mnet mnetxt setup guide
Post on 14-Apr-2015
Embed Size (px)
MVI56E-MNET / MNETXTControlLogix Platform Modbus TCP/IP Communication Module
April 18, 2011
Your Feedback PleaseWe always want you to feel that you made the right decision to use our products. If you have suggestions, comments, compliments or complaints about our products, documentation, or support, please write or call us.
How to Contact UsProSoft Technology 5201 Truxtun Ave., 3rd Floor Bakersfield, CA 93309 +1 (661) 716-5100 +1 (661) 716-5101 (Fax) www.prosoft-technology.com firstname.lastname@example.org Copyright 2011 ProSoft Technology, Inc., all rights reserved. MVI56E-MNET / MNETXT Setup Guide April 18, 2011 ProSoft Technology , ProLinx , inRAx , ProTalk , and RadioLinx are Registered Trademarks of ProSoft Technology, Inc. All other brand or product names are or may be trademarks of, and are used to identify products and services of, their respective owners.
ProSoft Technology Product DocumentationIn an effort to conserve paper, ProSoft Technology no longer includes printed manuals with our product shipments. User Manuals, Datasheets, Sample Ladder Files, and Configuration Files are provided on the enclosed CD-ROM, and are available at no charge from our web site: www.prosoft-technology.com
WarningsNorth America WarningsA B C D Warning - Explosion Hazard - Substitution of components may impair suitability for Class I, Division 2. Warning - Explosion Hazard - When in Hazardous Locations, turn off power before replacing or rewiring modules. Warning - Explosion Hazard - Do not disconnect equipment unless power has been switched off or the area is known to be nonhazardous. Suitable for use in Class I, Division 2 Groups A, B, C, and D, Hazardous Locations or Non-Hazardous Locations.
ATEX Warnings and Conditions of Safe Usage:Power, Input, and Output (I/O) wiring must be in accordance with the authority having jurisdiction A Warning - Explosion Hazard - When in hazardous locations, turn off power before replacing or wiring modules. B Warning - Explosion Hazard - Do not disconnect equipment unless power has been switched off or the area is known to be non-hazardous. C These products are intended to be mounted in an IP54 enclosure. The devices shall provide external means to prevent the rated voltage being exceeded by transient disturbances of more than 40%. This device must be used only with ATEX certified backplanes. D DO NOT OPEN WHEN ENERGIZED.
MarkingsHardware RatingsBackplane Current Load: 800 mA @ 5 Vdc; 3 mA @ 24 Vdc Operating Temperature: For standard MVI56E modules: 0 to 60 (32 to 140 C C F F) For MVI56E XT (conformal coated): -25 to 70 (-13 to 158 C C F F) Storage Temperature: -40 to 85 (-40 to 185 C C F F) Shock: 30 g operational; 50 g non-operational; Vibration: 5 g from 10 to 150 Hz Relative Humidity: 5% to 95% (without condensation) All phase conductor sizes must be at least 1.3 mm (squared) and all earth ground conductors must be at least 4mm (squared). MVI56E XT module comes with conformal coating installed.
Label Markings E183151 Class I, DIV 2, groups A,B,C,D T5 for all models 0 to +60 C C -25 to +70 (XT models only) C C II 3 G Ex nA T5 0